-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (ICSA-19-043-06) Siemens CP1604 and CP1616
13 February 2019
AusCERT Security Bulletin Summary
Product: Siemens CP1604 and CP1616
Operating System: Network Appliance
Impact/Access: Denial of Service -- Remote/Unauthenticated
Cross-site Request Forgery -- Remote with User Interaction
Cross-site Scripting -- Remote with User Interaction
Access Confidential Data -- Remote/Unauthenticated
CVE Names: CVE-2018-13810 CVE-2018-13809 CVE-2018-13808
- --------------------------BEGIN INCLUDED TEXT--------------------
Siemens CP1604 and CP1616
Original release date: February 12, 2019
All information products included in http://ics-cert.us-cert.gov are
provided"as is" for informational purposes only. The Department of Homeland
Security (DHS) does not provide any warranties of any kind regarding any
information contained within. DHS does not endorse any commercial product or
service, referenced in this product or otherwise. Further dissemination of this
product is governed by the Traffic Light Protocol (TLP) marking in the header.
For more information about TLP, see http://www.us-cert.gov/tlp/ .
1. EXECUTIVE SUMMARY
o CVSS v3 9.1
o ATTENTION : Exploitable remotely/low skill level to exploit
o Vendor : Siemens
o Equipment : CP1604 and CP1616
o Vulnerabilities : Cleartext Transmission of Sensitive Information,
Cross-site Scripting, Cross-site Request Forgery
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could result in a
denial-of-service condition and information exposure. An attacker could inject
unsuspecting user's systems, allowing an attacker to trigger actions via the
web interface that a legitimate user is allowed to perform.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
Siemens reports the following CP products are affected:
o CP 1604 and 1616: All versions prior to v2.8
3.2 VULNERABILITY OVERVIEW
3.2.1 CLEARTEXT TRANSMISSION OF SENSITIVE INFORMATION CWE-319
An attacker with network access to Port 23/TCP could extract internal
communication data or cause a denial-of-service condition.
CVE-2018-13808 has been assigned to this vulnerability. A CVSS v3 base score of
9.1 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:N/S:U/
3.2.2 IMPROPER NEUTRALIZATION OF INPUT DURING WEB PAGE GENERATION ('CROSS-SITE
The integrated web server of the affected CP devices could allow cross-site
scripting (XSS) attacks if unsuspecting users are tricked into following a
CVE-2018-13809 has been assigned to this vulnerability. A CVSS v3 base score of
6.1 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:R/S:C/
3.2.3 CROSS-SITE REQUEST FORGERY CWE-352
The integrated configuration web server of the affected CP devices could allow
a cross-site request forgery (CSRF) attack if an unsuspecting user is tricked
into accessing a malicious link.
CVE-2018-13810 has been assigned to this vulnerability. A CVSS v3 base score of
4.3 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:R/S:U/
o CRITICAL INFRASTRUCTURE SECTORS : Chemical, Critical Manufacturing, Energy,
Food and Agriculture,
Water and Wastewater Systems
o COUNTRIES/AREAS DEPLOYED : Worldwide
o COMPANY HEADQUARTERS LOCATION : Germany
Siemens reported these vulnerabilities to NCCIC.
Siemens recommends users update to version 2.8, which can be located here:
Siemens has identified the following specific workarounds and mitigations users
can apply to reduce the risk:
o Disable the integrated web server. The web server is disabled in the
default settings and its use is optional. Use in a productive environment
o Restrict access to the device to the internal or VPN network. Further
restrict access to the web interface (80/TCP) and to the telnet port (23/
TCP) to trusted IP addresses if possible.
o Do not click on links from unknown sources.
As a general security measure, Siemens strongly recommends protecting network
access to devices with appropriate mechanisms. In order to operate the devices
in a protected IT environment, Siemens recommends configuring the environment
according to Siemens' operational guidelines for industrial security ( https://
www.siemens.com/cert/operational-guidelines-industrial-security ), and
following the recommendations in the product manuals.
Additional information on industrial security by Siemens can be found at:
For more information on these vulnerabilities and associated software updates,
please see Siemens security advisory SSA-559174 on their website:
NCCIC recommends users take defensive measures to minimize the risk of
exploitation of this vulnerability. Specifically, users should:
o Minimize network exposure for all control system devices and/or systems,
and ensure that they are not accessible from the Internet .
o Locate control system networks and remote devices behind firewalls, and
isolate them from the business network.
o When remote access is required, use secure methods, such as Virtual Private
Networks (VPNs), recognizing that VPNs may have vulnerabilities and should
be updated to the most current version available. Also recognize that VPN
is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended
practices on the ICS-CERT web page. Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS-CERT website in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to NCCIC for tracking
and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to firstname.lastname@example.org
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: email@example.com
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----