-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (icsa-19-239-01) Delta Controls enteliBUS Controllers
28 August 2019
AusCERT Security Bulletin Summary
Product: enteliBUS Controllers
Operating System: Network Appliance
Impact/Access: Administrator Compromise -- Remote/Unauthenticated
CVE Names: CVE-2019-9569
- --------------------------BEGIN INCLUDED TEXT--------------------
ICS Advisory (ICSA-19-239-01)
Delta Controls enteliBUS Controllers
Original release date: August 27, 2019
All information products included in http://ics-cert.us-cert.gov are
provided"as is" for informational purposes only. The Department of Homeland
Security (DHS) does not provide any warranties of any kind regarding any
information contained within. DHS does not endorse any commercial product or
service, referenced in this product or otherwise. Further dissemination of this
product is governed by the Traffic Light Protocol (TLP) marking in the header.
For more information about TLP, see http://www.us-cert.gov/tlp/ .
1. EXECUTIVE SUMMARY
o CVSS v3 9.8
o ATTENTION: Exploitable remotely/low skill level to exploit
o Vendor: Delta Controls
o Equipment: enteliBUS Controllers
o Vulnerability: Buffer Overflow
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker on the
same network to gain complete control of the device's operating system and
allow remote code execution.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Delta Controls enteliBUS Controllers, industrial
control systems, are affected:
o enteliBUS Manager firmware Versions 3.40 R5 build 571848 and prior
o enteliBUS Manager Touch (eBMGR-TCH) firmware Versions 3.40 R5 build 571848
o enteliBUS Controller (eBCON) firmware Versions 3.40 R5 build 571848 and
3.2 VULNERABILITY OVERVIEW
3.2.1 BUFFER COPY WITHOUT CHECKING SIZE OF INPUT ('CLASSIC BUFFER OVERFLOW')
The affected products are vulnerable to a buffer overflow condition due to the
lack of input validation, which may allow an attacker to remotely execute
CVE-2019-9569 has been assigned to this vulnerability. A CVSS v3 base score of
9.8 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:N/S:U/
o CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities, Government
o COUNTRIES/AREAS DEPLOYED: Worldwide
o COMPANY HEADQUARTERS LOCATION: Canada
Douglas McKee @fulmetalpackets and contributing researcher Mark Bereza
@ROPsicle of McAfee Advanced Threat Research reported this vulnerability to
Delta Controls recommends users upgrade from enteliBUS 3.40 firmware to Version
3.40 R6 build 612850. Delta Controls also states it is important buildings are
updated to the 3.40 R6 release to mitigate risk. The firmware is only
accessible by Delta Controls registered partners and is not available for
public download. To acquire the firmware update, contact a Delta Controls
distributor or Delta Controls directly.
In addition to upgrading enteliBUS, Delta Controls recommends the following
actions to secure building sites:
o Do not leave building controllers exposed to the Internet.
If remote connections to the network are required, use a virtual
private network (VPN).
Secure networks using Tempered Networks products (available through
o Regularly review and validate the list of users authorized to access sites
o Ensure personnel with access to the system are knowledgeable about and are
trained to use Delta Controls products and networks.
o Follow security industry recommended practices for securing sites .
For more information on the vulnerability and more detailed mitigation
instructions, please see Delta Controls Security Bulletin "SecB0001: enteliBUS
3.40 Controllers Remote Code Execution Vulnerability." (Login required; only
accessible by Delta Controls registered partners and not available for public
CISA reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices
on the ICS webpage onus-cert.gov . Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS webpage on us-cert.gov in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to CISA for tracking
and correlation against other incidents.
No known public exploits specifically target this vulnerability.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to email@example.com
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: firstname.lastname@example.org
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----